- ENGINEERING INFO
- CASE STUDIES
As utilities tackle the challenges of rehabilitating and expanding water distribution and wastewater collection networks, they are increasingly turning to trenchless installation methods to reduce cost and minimize disruption to the public.
Jack-and-bore installation can be one of the most economical, reliable, and accurate ways to install a new cased pipe under established highways and railways without having to disrupt or impede the use of those arteries. The cost and sizing of a jack-and-bore installation is directly related to the largest cross section diameter of the carrier pipe. For example, if a design calls for a 24-inch PVC C905 bell and spigot carrier pipe, the designer must choose a casing size that will accommodate the OD of the segmented bell (~32 inches) and the OD of the bell restrainer (~35 inches). In this example, the designer would typically select a 42-inch steel casing to accommodate the restrained pipe section.
Designers have increasingly been electing to incorporate the Fusible PVC® family of pipe products into projects to provide an efficient, less costly jack-and-bore design. Inclusion of this option allows a designer to take advantage of the low profile, butt-fused PVC joint while still providing a restrained pipe design through the cased section. A Fusible PVC® pipe joint has a diameter that is nearly identical to the pipe barrel, making the casing size a function of the pipe barrel diameter instead of the bell or mechanical restraint diameter. As a result, casing designs using Fusible PVC® pipe as the carrier can utilize smaller casings than designs with segmented pipe. For example, 24-inch Fusible C-905® pipe has an outside diameter of 25.8 inches. The geometry of the pipe and fused joint allow it to easily fit within a 30-inch casing, where it can be placed directly on the flow line or installed with low profile casing insulators/spacers which allow for minor elevation adjustments as required.
By reducing the effective OD of the carrier pipe, a smaller casing pipe can be used; providing substantial savings to the owner while still achieving the desired design performance. This reduction in casing size has consistently delivered a 30-40% savings in jack-and-bore sections alone, compared to segmented carrier pipe designs. It is not uncommon to see $120-$150/LF installation savings with the smaller casing option in the example illustrated below: